09-02-2006, 08:19 PM
Join Date: Mar 2004
Location: Leverett, Mass
iTrader Positive Rating: 100%
Neat looking setup. Are you sure that last photo is a regulator? It looks to small, more like an on/off type valve to me.
If I understand correctly, you need an adaptor you can take to the gas store so they can refill it? I woudl first contact the guy you got it from and see if he knows anyone who can help you. I woudl imagine that even if Taiwan uses a wierd fitting that somewhere there are adaptors. If that fails, take the tank and a CGA 320 fitting to a machinist and see if they will make you an adaptor. Having one machined out of brass should not be too expensive. Lastly, but before you have one machined, see if the gas store will actually fill your tank with your adaptor and find out what you need to do when the hydro test is up.